Urgent ELECTRIC reveal reasons for complete extinction declares alert to restore powe
Urgent ELECTRIC reveal the reasons for the complete extinction declares alert to restore power
The Ministry of Electricity confirmed in an official statement that the complete extinction of the stream of electricity in Iraq, "announcing" a state of alert to restore power. "
According to a ministry statement received by all of Iraq [where] a copy of it, "the occurrence fully extinguished in the electrical system on Tuesday at 13:18 where they were extinguishing unit No. 1 in Nasiriyah Thermal Power Station made an emergency landing due to vibration of the turbine / coincided with the separation of Rumaila line - Nasserism 400 K. in one hand Nasiriyah and then ripped off line architecture - Wasit 400 kV from both sides, which led to a complete kind in all the provinces. "
The face of the Electricity Minister Qassim Fahdawi according to the statement to "mobilization of all cadres of the ministry to address the imbalance and return lines and ordered the formation of a committee to achieve the causes of the fire accident."
The ministry said "Now start working on the re-lines, respectively, where they were re-Kirkuk line - Diyala 400 kV line Diyala - east Baghdad, 400 kV, line-east of Baghdad - 400, north of Baghdad, and north of Baghdad - Holy of gas."
She added, "has also been re-Amin line - east of Baghdad 400 K Win, and operation of the unit No. 1 in the Khor Al-Zubair, and re-Amin line - Wasit thermal 400 kV, and re-Amin line - south of Baghdad, 400 No. 1 for work re north of Baghdad line -kds 2, and linking units 1, 3 and 4 in the creek, connecting the unit 2 in the SAA. "
An official source at the Ministry of Electricity announced the full amortization of the electricity in the whole of Iraq.
The source for [where] he was "not yet know the reasons for this interruption, but work is underway to restore the power."
The electricity distribution Directorate of Dhi Qar, today announced that a breakdown in the national system of electricity caused a complete interruption of energy in cities across the province.
According to Director of Information in the circuit Hossam Maaleh in a press statement, he said power witnessed in the province at about one and a half hour of the afternoon was interrupted because of the national system is fully out of work. "
He said the distribution of the Directorate is not aware of until now the reasons extinguish the national system, which is awaiting clarification from the ministry for the cause of the fire and the date of reemployment. "